Farmacia italiana online: acquisto cialis in Italia e Roma senza ricetta.
Microsoft word - datasheet - 12,8 volt lithium iron phosphate batteries - rev 04 - en.doc
1 2,8 Volt lithium iron phosphate batteries
Why lithium-iron phosphate?
Lithium-iron-phosphate (LiFePO4 or LFP) is the safest of the mainstream li-ion battery types. The nominal
voltage of a LFP cell is 3,2V (lead-acid: 2V/cell). A 12,8V LFP battery therefore consists of 4 cells connected in
series; and a 25,6V battery consists of 8 cells connected in series. Rugged
A lead-acid battery will fail prematurely due to sulfation if:
If it operates in deficit mode during long periods of time (i. e. if the battery is rarely, or never at all, fully charged).
If it is left partially charged or worse, fully discharged (yacht or mobile home during winter time).
12,8V 90Ah LiFePO4 battery
A LFP battery does not need to be fully charged. Service life even slightly improves in case of partial charge
instead of a full charge. This is a major advantage of LFP compared to lead-acid.
(cell balancing only)
Other advantages are the wide operating temperature range, excellent cycling performance, low internal
resistance and high efficiency (see below).
LFP is therefore the chemistry of choice for very demanding applications. Efficient
In several applications (especially off-grid solar and/or wind), energy efficiency can be of crucial importance.
The round trip energy efficiency (discharge from 100% to 0% and back to 100% charged) of the average lead-
acid battery is 80%.
The round trip energy efficiency of a LFP battery is 92%.
The charge process of lead-acid batteries becomes particularly inefficient when the 80% state of charge has
been reached, resulting in efficiencies of 50% or even less in solar systems where several days of reserve energy
is required (battery operating in 70% to 100% charged state).
In contrast, a LFP battery will still achieve 90% efficiency under shallow discharge conditions.
12,8V 90Ah LiFePO4 battery
Size and weight
(cell balancing and BMS interface)
Saves up to 70% in space
Saves up to 70% in weight Expensive?
LFP batteries are expensive when compared to lead-acid. But in demanding applications, the high initial cost
will be more than compensated by longer service life, superior reliability and excellent efficiency. Endless flexibility
LFP batteries are easier to charge than lead-acid batteries. The charge voltage may vary from 14V to 16V (as long
as no cell is subjected to more than 4,2V), and they do not need to be fully charged. Therefore several batteries
can be connected in parallel and no damage will occur if some batteries are less charged than others. With or without Battery Management System (BMS)?
1. A LFP cell will fail if the voltage over the cell falls to less than 2,5V.
2. A LFP cell will fail if the voltage over the cell increases to more than 4,2V.
Lead-acid batteries will eventually also be damaged when discharged too deeply or overcharged, but not
immediately. A lead-acid battery will recover from total discharge even after it has been left in discharged state
during days or weeks (depending on battery type and brand).
3. The cells of a LFP battery do not auto-balance at the end of the charge cycle.
The cells in a battery are not 100% identical. Therefore, when cycled, some cells will be fully charged or
discharged earlier than others. The differences will increase if the cells are not balanced/equalized from time to
In a lead-acid battery a small current will continue to flow even after one or more cells are fully charged (the
main effect of this current is decomposition of water into hydrogen and oxygen). This current helps to fully
charge other cells that are lagging behind, thus equalizing the charge state of all cells.
The current through a LFP cell however, when fully charged, is nearly zero, and lagging cells will therefore not
be fully charged. The differences between cells may become some so extreme over time that, even though the
overall battery voltage is within limits, some cells will be destroyed due to over- or under-voltage. Cell balancing
is therefore highly recommended.
In addition to cell balancing, a BMS will:
Prevent cell under voltage by timely disconnecting the load.
Prevent cell overvoltage by reducing charge current or stopping the charge process.
Shut down the system in case of over temperature.
A BMS is therefore indispensable to prevent damage to large Li-ion battery banks.
With cell balancing, but without BMS: 12,8V LFP batteries for light duty applications
In applications were excessive discharge (to less than 11V), overcharge (to more than 15V) or excessive charge current will never occur,
12,8V batteries with cell balancing only may be used.
Please note that these batteries are not suitable for series or parallel connection.
A Battery Protect module (see www.victronenergy.com) may be used to prevent excessive discharge.
The current draw of inverters and inverter/chargers is often still significant (0,1A or more) after low voltage shutdown. The remaining stand-by current will therefore damage the battery if the inverters or inverter/chargers are left connected to the battery after low voltage shutdown during a long period of time.
With cell balancing and interface to connect to a Victron BMS: 12,8V LFP batteries for heavy duty applications and
These batteries have integrated Cell Balancing, Temperature and Voltage control (BTV). Up to ten batteries can be paralleled and up to
four batteries can be series connected (BTV’s are simply daisy-chained) so that a 48V battery bank of up to 2000Ah can be assembled.
The daisy-chained BTV’s must be connected to a battery management system (BMS). Battery Management System (BMS)
The BMS connects to the BTV’s and its essential functions are:
Disconnect or shut down the load whenever the voltage of a battery cell falls to less than 2,5V.
Stop the charging process whenever the voltage of a battery cell increases to more than 4,2V.
Shut down the system whenever the temperature of a cell exceeds 50°C.
More features may be included: see the individual BMS datasheets.
Cell balancing only
Cell balancing and BMS interface
discharge current Recommended continuous
-20°C to +50°C (do not charge when battery temperature < 0°C)
Between 14V and 15V (<14,5V recommended)
Victron Energy B.V. | De Paal 35 | 1351 JG Almere | The Netherlands
General phone: +31 (0)36 535 97 00 | Fax: +31 (0)36 535 97 40
E-mail: firstname.lastname@example.org | www.victronenergy.com
MINISTERIO DEL INTERIOR Créase en su ámbito un Comité de Elegibilidad para Refugiados. Funciones. DECRETO Nº 464 VISTO las Leyes números 15.869, 17.468 y 23.160, mediante las cuales la República Argentina formula su adhesión a la Convención de las Naciones Unidas de 1951 y al Protocolo de 1967 sobre el Estatuto de los Refugiados, respectivamente, y Que dichos instrumento
Anesthesia and postoperative analgesia after percutaneous hallux valgus repair inAnesthe´sie et analge´sie postope´ratoire apre`s chirurgie de l’hallux valgus par voie percutane´e enF. Adam E. Pelle-Lancien , T. Bauer N. Solignac D.I. Sessler M. Chauvin a De´partement d’anesthe´sie-re´animation, hoˆpital Ambroise-Pare´, Assistance publique–Hoˆpitaux de Paris, 9, avenue Charles-d